Often overlooked in boiler operation is the establishment and enforcement of a procedure for keeping adequate boiler logs. The management of a facility which has a boiler plant bears the responsibility for implementing and maintaining this procedure.
Over a period of time, boiler operating logs help distinguish operating trends that can allow problems to be diagnosed, and boiler and/or fuel-burning system maintenance to be scheduled, before an emergency shutdown is necessary. For example, a steady rise in stack temperature, at the same boiler load, indicates dirty boiler firesides or water side scale build-up. In either case remedial action can be taken before it is necessary to shut the unit down for cleaning.
There are two types of boiler logs: one for daily operations, the other for maintenance activities. These logs can be easily customized for the particular installation and its unique requirements. Using a computer or a word processor, it is a relatively simple matter to prepare a customized log form. Items which might be included are shown in the guidelines below. This material is by no means inclusive; items may be added or deleted as needed for the specific installation.
Log sheets are also available from boiler insurance companies. Maintenance logs should include those items recommended in the boiler and burner manufacturer’s operating instructions.
The National Board Incident Report for 1993 indicates that 79 percent of all reported boiler accidents for the three boiler categories are attributable to just two causes: low water cutoffs, and operator error/poor maintenance. Proper keeping and analysis of boiler logs help operators to focus on these areas, and therefore reduce boiler accidents. As low-water-cutoff problems account for 62 percent of the incidents, maintenance and testing of these devices could cause a dramatic reduction in boiler accidents.
A separate log sheet is required for each boiler in the facility. One option is having a log sheet that is good for one month (31 days), and provides for two sets of readings per day. It is recommended that completed logs be three-hole punched and filed in a loose-leaf notebook for future analysis. Management should establish a reasonable period of time for log retention, consistent with the life expectancy of the unit.
Make provisions on the sheets for recording weekly and monthly checks with the date of completion. A general comments section allows significant events, such as the date of the annual boiler inspection, to be recorded. Other events such as boiler malfunctions should also be noted.
Logs for high-pressure boilers are similar, but provide for at least three readings (one per shift) per day. High-pressure logs normally require additional readings consistent with the system.
Items which might be considered for a customized log are shown below. The most important concern is to keep the log completely, accurately, and updated regularly. Too often, logs are kept with identical readings for an entire month or with gaps in the readings. Management must stress the need for complete, accurate logs, and must also explain the need for analysis and its benefits.